Pool clearances around power lines
National Electrical Safety Code requires a 22.5 foot clearance in any direction from the water level, edge of pool, diving platforms, pool sliding boards or other fixed pool-related structure to the overhead electric service line, and a 25-foot clearance from overhead primary lines. The code applies to in-ground and above-ground pools, hot tubs, and the like.
*All pools must be a minimum of 5 feet away from any underground electric cables. Call before you set up any in-ground or above ground pool or hot tub to be sure clearances are met. Before digging for any pool or yard project, call 811 to have underground cables located.
Failure to check clearances can result in additional expense if we have to move any of our lines and facilities or if the pool or hot tub must be moved to comply with the National Electrical Safety Code.
The clearances are designed to protect swimmers and people using rescue and skimmer poles, which are typically aluminum, and to keep the path clear for utility workers.